Field Demonstration of Ground-Source Integrated Heat Pump Part I. Technology and Field Demo System/Site Descriptions, and Preliminary Summer/Fall Performance Analysis for One Site
The field study is planned to continue through the 2016 cooling season with the draft final project report due by September 30, 2016. This report provides a description of both installations and preliminary 2015 cooling and fall season performance results for the Knoxville site. For the August 18 through December 14 period, the Knoxville site GS-IHP provided 53.6% total source energy savings compared to a baseline electric RTU/heat pump and electric WH. Peak demand savings ranged from 33% to 59% per month. Energy cost savings of 53.1% have been achieved to date with more than half of that coming from reduced demand charges. Data on installation and maintenance costs are being collected and will be combined with total test period energy savings data for a payback analysis to be included in the project final report. The GS-IHP also saved a significant amount of carbon emissions. The total emission savings for the Knoxville site for the August-December 2015 period were ~0.8 metric tons. If trading for carbon credits ever becomes a reality, additional cost savings would be realized.
- Publication Date:
- OSTI Identifier:
- Report Number(s):
- DOE Contract Number:
- Resource Type:
- Technical Report
- Research Org:
- Oak Ridge National Lab. (ORNL), Oak Ridge, TN (United States). Building Technologies Research and Integration Center (BTRIC)
- Sponsoring Org:
- USDOE Office of Energy Efficiency and Renewable Energy (EERE)
- Country of Publication:
- United States
- 20 FOSSIL-FUELED POWER PLANTS
Enter terms in the toolbar above to search the full text of this document for pages containing specific keywords.