Lagoon Seepage Testing Report for Central Facilities Area (CFA) Sewage Lagoons at Idaho National Laboratory, Butte County, Idaho
J-U-B ENGINEERS, Inc. (J-U-B) performed seepage tests on the CFA Wastewater Lagoons 1, 2, and 3 between August 26th and September 22nd, 2014. The lagoons were tested to satisfy the Idaho Department of Environmental Quality (DEQ) Rules (IDAPA 58.01.16) that require all lagoons be tested at a frequency of every 10 years and the Compliance Activity CA-141-03 in the DEQ Wastewater Reuse Permit for the CFA Sewage Treatment Plant (LA-000141-03). The lagoons were tested to determine if the average seepage rates are less than 0.25 in/day, the maximum seepage rate allowed for lagoons built prior to April 15, 2007. The average seepage rates were estimated for each lagoon and are given in Table-ES1. The average seepage rates for Lagoons 1 and 2 are less than the allowable seepage rate of 0.25 in/day. Lagoon 1 and 2 passed the seepage test and will not have to be tested again until the year 20241. However, the average seepage rate for Lagoon 3 appears to exceed the allowable seepage rate of 0.25 in/day which means the potential source for the excessive leakage should be investigated further.
- Publication Date:
- OSTI Identifier:
- Report Number(s):
- DOE Contract Number:
- Resource Type:
- Technical Report
- Research Org:
- Idaho National Lab. (INL), Idaho Falls, ID (United States)
- Sponsoring Org:
- USDOE Office of Nuclear Energy (NE)
- Country of Publication:
- United States
- 99 GENERAL AND MISCELLANEOUS Central Facilities Area; CFA STP Seepage Test; JUB Engineers; Lagoon Seepage Test; Sewage Treatment Plant
Enter terms in the toolbar above to search the full text of this document for pages containing specific keywords.