Measure Guideline: Implementing a Plenum Truss for a Compact Air Distribution System
This Measure Guideline presents the steps to implement a compact duct system inside an attic bulkhead (plenum truss) of a one-story, slab-on-grade (SOG) home. In a compact duct design, ductwork runs are reduced in length to yield a smaller and more compact duct system. Less energy will be lost through ductwork if the ducts are contained within the thermal enclosure of the house. These measures are intended for the production builder working to meet the 2012 International Energy Conservation Code (IECC) requirements and keep the ductwork within the thermal enclosure of the house. This measure of bringing the heating, ventilation and air conditioning (HVAC) equipment and ductwork within the thermal enclosure of the house is appropriate for the builder wishing to avoid cathedralizing the insulation in the attic space (i.e., locating it at the underside of the roof deck rather than along the attic floor) or adding dropped soffits.
- Publication Date:
- OSTI Identifier:
- Report Number(s):
- DOE Contract Number:
- Resource Type:
- Technical Report
- Resource Relation:
- Related Information: Work performed by IBACOS, Inc., Pittsburgh, Pennsylvania
- Research Org:
- National Renewable Energy Laboratory (NREL), Golden, CO.
- Sponsoring Org:
- USDOE Office of Energy Efficiency and Renewable Energy Building Technologies Office
- Country of Publication:
- United States
- 32 ENERGY CONSERVATION, CONSUMPTION, AND UTILIZATION COMPACT DUCT SYSTEM; COMPACT AIR DISTRIBUTION SYSTEM; HEATING, VENTILATION, AND AIR CONDITIONING (HVAC); INSULATION; REVERSE ATTIC BULKHEAD; PLENUM TRUSS; Buildings
Enter terms in the toolbar above to search the full text of this document for pages containing specific keywords.