Imatran Voima Oy, IVO, operates two VVER 440 reactors. Unit 1 has been operating since 1977 and unit 2 since 1981. First damages of the feed water distribution (FWD) pipes were observed in 1989. In closer examinations FWD-pipe T-connection turned out to suffer from severe erosion corrosion damages. Similar damages have been found also in other VVER 440 type NPPs. In 1994 the first new FWD-pipe was replaced and in 1996 extensive water hammer experiments were carried out together with EDO Gidropress in Podolsk. After the first phase of the experiments some fundamental changes were made to the construction of the FWD-pipe. The object of this paper is to give short insight to the design of the new FWD-pipe concentrating on water hammer experiments. (orig.).