The article gives a detailed description of the construction and the operation of the 290 MW air-storage gas-turbine power station at the town of Huntorf. The cavities of a 300,000 cbm storage capacity needed for accomodating compressed air have been solution-mined in a salt dome at a depth of c. 700 m. The air-mass-flow-controlled gas turbine consists of a 6-stage HP part and a 5-stage LP part with a combustion chamber each. The turbine is used to cover peak loads, whereas slack periods are covered by the generator which drives to air compressors connected in series to refill the underground compressed-air stores. Since December 1978, the plant has been in operation. As a gas turbine, it has attained a high level of start frequency, indeed, with its 400 starts within the first 5 months. Energy cost of this power station range within the optimum (between half and full load) at about 70% of the energy cost required by a conventionally natural-gas-fired turbine.