Fracture of the rubber diaphragm in a liquid relief valve initiated events leading to a loss of coolant in Unit 2, on December 10. The valve failed open, filling the bleed condenser. The reactor shut itself down. When pressure recovered, two spring-loaded safety relief valves opened and one of them chattered. The shock and pulsations cracked the inlet pipe to the chattering valve, and the subsequent loss of coolant triggered the emergency core cooling system. The incident was terminated by operator action. No abnormal radioactivity was released. The four reactor units of Pickering A remained shut down until the corrective actions were completed in April/May 1995. (author). 4 figs.