A milk cow gives off 35.7 kW h/d via its body, excreta and urine. 68.4% of this is body heat. Part of this waste heat escapes with the waste air from the cowsheds. The heat can be recovered from the waste air by an air/air heat exchanger. The air is collected and taken to a heat exchanger. In the heat exchanger, fresh air is heated by the waste air, and is distributed over the cowshed by a system of ducts. The heated waste air escapes through a central chimney at the end of the heat exchanger. It is sensible to fit the heat exchanger above the cowshed roof, if there is sufficient space available and the chimney should run upwards from the cowshed. A double heat exchanger makes it possible to allocate each half of the cowshed to half of the heat exchanger.