Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 5. Probabilistic fracture mechanics analysis. Load Combination Program Project I final report
Abstract
The primary purpose of the Load Combination Program covered in this report is to estimate the probability of a seismic induced LOCA in the primary piping of a commercial pressurized water reactor (PWR). Best estimates, rather than upper bound results are desired. This was accomplished by use of a fracture mechanics model that employs a random distribution of initial cracks in the piping welds. Estimates of the probability of cracks of various sizes initially existing in the welds are combined with fracture mechanics calculations of how these cracks would grow during service. This then leads to direct estimates of the probability of failure as a function of time and location within the piping system. The influence of varying the stress history to which the piping is subjected is easily determined. Seismic events enter into the analysis through the stresses they impose on the pipes. Hence, the influence of various seismic events on the piping failure probability can be determined, thereby providing the desired information.
 Authors:
 Publication Date:
 Research Org.:
 Lawrence Livermore National Lab., CA (USA); Science Applications International Corp., La Jolla, CA (USA)
 OSTI Identifier:
 5341468
 Report Number(s):
 NUREG/CR2189Vol.5; UCID18967Vol.5
ON: TI85016245
 DOE Contract Number:
 W7405ENG48
 Resource Type:
 Technical Report
 Country of Publication:
 United States
 Language:
 English
 Subject:
 22 GENERAL STUDIES OF NUCLEAR REACTORS; 21 SPECIFIC NUCLEAR REACTORS AND ASSOCIATED PLANTS; LOSS OF COOLANT; DYNAMIC LOADS; PIPES; FAILURES; FRACTURE MECHANICS; PRIMARY COOLANT CIRCUITS; PWR TYPE REACTORS; SEISMIC EFFECTS; CRACKS; REACTOR SAFETY; STRESS ANALYSIS; WELDED JOINTS; ACCIDENTS; COOLING SYSTEMS; ENERGY SYSTEMS; JOINTS; MECHANICS; REACTOR ACCIDENTS; REACTOR COMPONENTS; REACTOR COOLING SYSTEMS; REACTORS; SAFETY; WATER COOLED REACTORS; WATER MODERATED REACTORS; 220900*  Nuclear Reactor Technology Reactor Safety; 210200  Power Reactors, Nonbreeding, LightWater Moderated, Nonboiling Water Cooled
Citation Formats
Harris, D.O., Lim, E.Y., and Dedhia, D.D. Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 5. Probabilistic fracture mechanics analysis. Load Combination Program Project I final report. United States: N. p., 1981.
Web. doi:10.2172/5341468.
Harris, D.O., Lim, E.Y., & Dedhia, D.D. Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 5. Probabilistic fracture mechanics analysis. Load Combination Program Project I final report. United States. doi:10.2172/5341468.
Harris, D.O., Lim, E.Y., and Dedhia, D.D. 1981.
"Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 5. Probabilistic fracture mechanics analysis. Load Combination Program Project I final report". United States.
doi:10.2172/5341468. https://www.osti.gov/servlets/purl/5341468.
@article{osti_5341468,
title = {Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 5. Probabilistic fracture mechanics analysis. Load Combination Program Project I final report},
author = {Harris, D.O. and Lim, E.Y. and Dedhia, D.D.},
abstractNote = {The primary purpose of the Load Combination Program covered in this report is to estimate the probability of a seismic induced LOCA in the primary piping of a commercial pressurized water reactor (PWR). Best estimates, rather than upper bound results are desired. This was accomplished by use of a fracture mechanics model that employs a random distribution of initial cracks in the piping welds. Estimates of the probability of cracks of various sizes initially existing in the welds are combined with fracture mechanics calculations of how these cracks would grow during service. This then leads to direct estimates of the probability of failure as a function of time and location within the piping system. The influence of varying the stress history to which the piping is subjected is easily determined. Seismic events enter into the analysis through the stresses they impose on the pipes. Hence, the influence of various seismic events on the piping failure probability can be determined, thereby providing the desired information.},
doi = {10.2172/5341468},
journal = {},
number = ,
volume = ,
place = {United States},
year = 1981,
month = 6
}

This volume describes the computational methodology used to estimate the probability of a simultaneous occurrence of an earthquake and a primary coolant loop pipe fracture caused directly by an earthquake for a pressurized water reactor. Point estimates of this probability, based on a simulation experiment, and the probabilities of related events are included. Simulation is used to estimate weld fracture probabilities conditional on a crack initially existing and an earthquake of specified intensity occurring at a specified time in the life of the plant. These estimates are combined with probabilities associated with the occurrence of an earthquake and the existencemore »

Probability of pipe fracture in the primary coolant loop of a PWR Plant. Volume 2. Primary Coolant Loop Model. Load Combination Program, Project I final report
This report describes the Zion Station reactor coolant loop model developed by Sargent and Lundy Engineers for Lawrence Livermore National Laboratory as part of its Load Combination Program. This model was developed for use in performing seismic time history analyses of an actual pressurized water reactor (PWR) system. It includes all major items affecting the seismic response of a 4loop Westinghouse nuclear steam supply system: the components, supports, and interconnecting piping. The model was further expanded to permit static analysis of dead weight, thermal, and internal pressure load conditions. 7 refs., 42 figs., 9 tabs. 
Probability of pipe fracture in the primary coolant loop of a PWR Plant. Volume 3. Nonseismic stress analysis. Load Combination Program, Project I final report
This volume describes the analyses used to evaluate stresses due to loads other than seismic excitations in the primary coolant loop piping of a selected fourloop pressurized water reactor nuclear power station. The results of the analyses are used as input to a simulation procedure for predicting the probability of pipe fracture in the primary coolant system. Sources of stresses considered in the analyses are pressure, dead weight, thermal expansion, thermal gradients through the pipe wall, residual welding, and mechanical vibrations. Stresses due to dead weight and thermal expansion are computed from a threedimensional finite element model that uses amore » 
Probability of pipe fracture in the primary coolant loop of a PWR Plant. Volume 6. Failure mode analysis load combination program. Project I, final report
Material properties and failure criteria were evaluated to assess the requirements for doubleended guillotine break in the primary coolant loop of the Zion Unit 1 pressurized water reactor. The properties of the 316 stainless steel piping materials were obtained from the literature. Statistical distributions of both the tensile and fracture properties at room and operating temperatures were developed. Yield and ultimate strength tensile properties were combined to estimate the material flow strength. The flow strength and fracture properties were used in the various failure models analyzed. Linearelastic, elasticplastic, and fully plastic fracture models were compared, and the governing fracture criterionmore » 
Probability of pipe fracture in the primary coolant loop of a PWR plant. Volume 4. Seismic response analysis. Load Combination Program Project I final report
This volume of the report gives a detailed account of the seismic response analysis of the primary coolant loop piping of Unit 1 of the Zion Nuclear Power Station. Because the purpose of this work was to perform a realistic simulation, best estimate loads and material properties were used for the calculation whenever possible. When such data were unavailable, conservative values were used. The calculation procedure included the generation of seismic input, the determination of dynamic soil properties, a threepart soilstructurepiping interaction analysis, and the postresponse data procession. A large number of variables considered in the analysis can affect themore »